Neon lamp unit with N terminal Light control, grey
Product description Neon lamp unit with N terminal Main design line Light control grey 230 V~, 1 mA Operating voltage 230 Rated current 1 mA Lighting for lighting and monitoring circuit Rocker switch/rocker push-button for pullcord switch Combination rocker switches/rocker push-buttons for series switch illuminated Information text When several neon lamp units are used, the lamp current may result in malfunctioning of the relay/pulse relay. Remedy: Carry along a neutral conductor or connect a capacitor 230 V (1 µF per 10 mA neon lamp current) in parallel with the coil. Information text, image price list/catalogue suitable for push-button and pullcord switches as well as rocker switches and rocker push-buttons from the years 1985 to 1995. ; Not suitable for water-protected, flush-mounted installation IP44. Refer to the overview for the matching flush-mounted inserts.
All data is subject to errors and technical modifications.