Neon lamp unit with N terminal Light control, grey
Lighting for lighting and monitoring circuit Refer to the overview for the matching flush-mounted inserts. Information text When several neon lamp units are used, the lamp current may result in malfunctioning of the relay/pulse relay. Remedy: Carry along a neutral conductor or connect a capacitor 230 V (1 µF per 10 mA neon lamp current) in parallel with the coil. Information text, image price list/catalogue Not suitable for push-button and pullcord switches, rocker switches and rocker push-buttons from the years 1985 to 1995. Product description Neon lamp unit with N terminal grey Main design line Light control
All data is subject to errors and technical modifications.